What can happen when backflow preventers and flash arresters aren't checked?
Return to Kris Bancroft Home Page
Backflow preventers should be checked each time a new tank is hooked up. Flash arresters should be checked at least once every six months of use and by a service trained to do so. Both should be checked when there is reasonable suspicion that damage might have occurred.
Last updated: November 23, 2001